We’ve put together a list of some frequently asked questions about our PQube 3. Check back often for updates or email us at firstname.lastname@example.org if you have a question you’d like answered.
Every morning at 4:30 AM local time, the PQube 3 copies the recorded files of the previous day’s trends and events to the external SD card. The folder structure copied is identical to the folder structure accessible via FTP, i.e. year, month, day. Automatic SD backup is an option that can be activated with the PQube configurator using firmware 3.5.6 and above.
There are two ways to check the amount of data:
The maximum length of wire recommended for a split-core CT and a PQube 3 is 500 ft (152 m).
Copy the Setup.ini file onto the USB stick that comes with the PQube. Insert the USB into the top USB slot located underneath the blue lid. This will activate an onscreen message stating a new Setup has been detected. Press YES to apply. The PQube 3 will automatically restart and apply the settings.
How to download data from a PQube 3 using a USB or microSD card.
• Using a USB, select SAVE FILES, USB, and choose TODAY, THIS WEEK, LAST WEEK, THIS MONTH or LAST MONTH.
• Using a microSD, the data is automatically backed up nightly. The card may fill up over time so it’s a good idea to check the card and clear space as needed.
When downloading data, there are no date ranges. However, you can use the FREE Report Writer program to generate a report based on a date range.
No. The FTP function on the PQube 3 is designed for transferring files only. To delete files from your PQube 3, use the CLEAR DATA function using a web page and the PQube 3 display.
When the PQube 3’s internal memory reaches 75%, it will automatically delete older data to free up space for new data.
Power off the unit. Wipe the accessible parts of your PQube 3 with a slightly damp lint-free cloth. Do not use abrasives or chemical cleaners.
Contact Powerside Technical support to order the replacement battery. Once received, follow these steps:
The estimated life expectancy of a PQube 3 and PM1 module is 10 years based on an operating temperature of 20-30 degrees Celsius.
A PQube 3 does not have an on/off switch because it is designed to run continuously.
A PQube 3 doesn’t automatically download files via FTP to a workstation or server. You need to manually initiate an FTP client session with the PQube to start the transfer of files. However, some third-party solutions to share. Use CN Rood’s DSS Platform or Tectra’s MPMS software program both will automatically initiate downloads.